Lightning Arrester Guard Installation Guide
DE-ENERGIZED INSTALLATION NOTES
Align one side of the Reliaguard Bushing Guard under the bushing’s uppermost shed. If installing Reliaguard GreyEEL® conductor guard onto conductor, refer to the GreyEEL® installation guide prior to alignment.
If using the vertical conductor exit, squeeze latch to open one side of the Lightning Arrester Guard’s hinge. Feed conductor through the top, reattach hinge.
Close the bottom arrow latches, ensuring only one shed is contained within the guard. Push guard together on both sides until arrow latches fully snap. The arrow heads will be fully visible outside the square receptacles.
Thru-holes are provided for the optional use of push pins or zip ties as a secondary closure. These are not required for retention and are provided only for convenience of users who prefer a secondary closure method.
DE-ENERGIZED REMOVAL NOTES
Remove Lightning Arrester Guard by clipping off the heads of push pins or zip ties with suitable cutter. Press in arrow latch snaps as indicated, to separate.